|Fluid Category 3 - Size||15 mm|
|Fluid Category 3 - Powered||No|
|Fluid Category 3 - Test Points||Verifiable|
Filling and topping up of- Primary Heating Systems; Under Floor Heating; Refrigerating Equipment; Chilled Water Circuits; Industrial Processes.
Downloads & Resources
The primary sealed heating system shall be filled and pressurised by an Autofill pressurisation unit – model AFCA - with high and low pressure fault lamps - as manufactured and commissioned by Arrow Valves Ltd - Tel 01442 823123 www.arrowvalves.co.uk . The unit shall incorporate a manual quick fill / flushing valve and a pressure reducing valve, which allows the system to be filled without electrical power with Fluid Category 3 protection for systems up to 45 kW - an external quick fill facility is not required. The quick fill rate shall be 1800 litres per hour @ 1 bar pressure differential. The automatic filling device is to be connected to the mains or, where the mains supply pressure is insufficient for the static head required, the unit shall be supplied from the boosted cold water service if available. The manufacturer’s flexible hoses incorporating a servicing valve shall be used. A double check valve is not required. Automatic filling shall be via a solenoid valve and pressure switch. The cold fill switch-on pressure shall be 0.2 bar more than the static head of the system. The unit shall incorporate lamps to indicate filling and standby conditions. The base of the cabinet must be 300 – 1500 mm above the floor and adequate access shall be provided for testing. The outlet from the unit must be connected to the primary circuit return before the circulation pump. A DN32 discharge pipe must be connected to the integral tundish and taken to a gully. Amend as required  Delete if lamps not required.