|Fluid Category 5 / Booster Pumps - Max. Flow Rate||No|
|Fluid Category 5 / Booster Pumps - Outlet Pressure||No|
|Fluid Category 5 / Booster Pumps - Inlet Size||No|
|Fluid Category 5 / Booster Pumps - Outlet Size||No|
|Fluid Category 5 / Booster Pumps - Voltage||No|
|Fluid Category 5 / Booster Pumps - Number of Pumps||No|
|Fluid Category 5 / Booster Pumps - Cistern Size||No|
|Fluid Category 5 / Booster Pumps - Powered||No|
Penthouse (3 storey and taller); Boosting low water pressure; ?Combi? boilers & showers.
Downloads & Resources
A Booster Pump Set “Pent-A-Boost” shall be installed – model BTAF1200 - as manufactured and distributed by Arrow Valves Ltd - Tel 01442 823123 www.arrowvalves.co.uk. The unit shall have an 18 litre cistern, with a lid and screened DN40 overflow complying with G16.13 of the Water Regulations. The pump shall be centrifugal with stainless steel impellors and housing with an input power of 1200 W and a closed valve head of 5.7 bar and be controlled by a pressure switch connected to a 24 litre pressure vessel. The cistern level shall be controlled automatically by a servo solenoid valve operated via stainless steel conductive electrodes and controller. A low-level pump cut-out shall be controlled by electrodes in the cistern, which shall automatically reset once the cistern is sufficiently full. The cistern shall feature a high-level alarm linked to a volt free BMS relay – model BTBMS1. The unit shall feature a stainless steel base plate and be acoustically attenuated by anti-vibration feet and stainless steel braided flexible hoses. A 28 mm supply is required, which must maintain a dynamic pressure of 1.0 bar.